Steambath Generator for Steamroom - Fixed Kilowatt
Stainless Steel Tank ensures years of dependable service
Every generator factory-tested before shipment to meet Steamist's high-quality stanadards.
Designed for energy-efficient, money -saving operation.
The industry's most comprehensive Warranty
Dual Kilowatt Generators- These generators are equipped with a unique power level switch, which enables the user to adjust the kw output of the generator to their exact comfort level and operates on a 30-minute Time Cycle.
20" L x 8.25"W x 18.25" H
Volts: 240 Volts
Max Amps: 29
Wire Size: 8
Line Fuse: 80
Maximum Cubic Foot Range: 450
To select the proper steam generator, you must factor in the size of the steamroom and make adjustments based on heat loss factors determine by the steamroom's location and construction materials.
Step 1: Calculate Cubic Footage - Measure length, width and height of bath or shower enclosure (steamroom) , multiply to determine cubic footage. (Example: 4' x 5' x 8' = 160 cu. ft.) Import: Celing height must not exceed 9'
Step 2: Determine Heat Loss Factory: Consider construction materials used in steamroom; find head loss multiplier below. Multiply by cubic footage. When there is more than one type of material, use the one with the higher heat loss factor. (Example: Ceramic Tile: 160 cu. ft. x 1.3 = 208 cu. ft.)
(Ceramic Tile - 1.3) (Glass Tile or Glass Block Walls - 1.35) (Porcelain Tile - 1.6) (Natural Stne Tiles up to 1/2" - 2.0) (Natural Stone Slabs over 1/2" - 2.25)
Step 3: Additional Heat Loss Factors - Insulated Exterior Walls - add an additional multiplier (1.10 per outside wall) is required for each exterior wall surrounding the steamroom. (Example: 200 cu. ft. x 1.10 = 220 cu. ft.)
Step Four: Select Model - Select the Generator with a Maximum Cubic Foot Range that is equal to or greater than your calculated Total Adjusted Cubic Feet.
Note 1: For celing heights over 8 feet but not more than 9 feet, use the next larger size generator.
Note 2: If the steamroom has a skylight or an outside window, select the next larger size generator. The skylight or window must be double-pane and sealed from insde the steamroom.
Note: Generator voltage must match exisiting utilities (208 or 240) volt)
Note: Steamist recommends that the SM-11 Generator have a thermostatic cntrol (TC-150, TC-135, DSC-425 or DSP Package)
Manufacturer's Warranty Included
Specifications & Diagrams:
A specifications document is currently not available for download. If you do not find the information you seek here, ask one of our experts »
*Discontinued - This product has been discontinued by the manufacturer and is Non-Returnable.
*Image displayed for product may differ from actual product appearance, especially in finish. Due to the differences in monitors, technical factors, and characteristics of some finishes, the colors shown here cannot be represented with all their true qualities. The images and color tiles should only be considered a guide. eFaucets.com is unable to guarantee that finishes between manufacturers will match.
*Orders placed before 3:00 pm (CST) Mon - Fri are usually shipped out the same business day when availability is displayed as 5 or greater. All orders subject to stock on hand.